Microfiche records prior to 2006 have not been completely digitized and may not be available yet on PRO. If you can not find what you are looking for please submit a records request.
Inspection History Details
1515 E AJO WY
Inspection Status: Approved
Inspection History: FIRE SPKLR - FINAL
Permit Number - T14BU00252
Inspection Description - FIRE SPKLR - FINAL
Inspection Status - Approved
|07/22/2014||FIRE SPKLR - FINAL||Approved|
|07/03/2014||FIRE SPKLR - FINAL||Partial Approval||fire pump test passed.
still need to run pump when alarm is hooked up and test all tampers.
|07/02/2014||FIRE SPKLR - FINAL||Denied||1. fire pump installed backwards.|